Before any lighting installations are carried out in bathrooms it is essential to understand the significance of bathroom zones, as set out in the electrical safety regulations. These bathroom zones are designed to ensure that only bathroom lights provided with appropriate protection are used, especially within the higher risk areas so that the risk of harm is avoided.
Like other electrical equipment, light fittings are given an IP Rating to indicate their suitability for a particular environment. IP stands for ingress protection and the rating consists of the letters IP followed by a two digit number. The first number indicates the level of protection provided against intrusion by solid objects such as dirt or dust. The second digit indicates the level of protection against various degrees of moisture. For a more in-depth explanation of IP Ratings take a look at our definitive guide to IP Ratings.
Bathroom Zones Explained
Bathroom zones are best described with reference to illustrations but the measurements stated are quite specific and must be adhered to. What follows should help with understanding what grade of fittings can be placed in the different bathroom zones and the reasons why. It is only a guide and such work should always be carried out by a qualified electrician who will be conversant with the IEE Wiring Regulations (17th Edition).
As you can see the illustration below shows a bath, wash basin and a stand-alone shower installation. If any of them are combined or their respective zones overlap then the higher risk level should be applied.
As you can see the illustrations show four distinct bathroom zones, 0, 1, 2 and 3 (referred to in the key as “Outside Zones”).
Bathroom Zone 0
Zone 0 is inside the bath or the shower tray itself. If lighting is required in there, any fitting used must use a low voltage supply, that is a maximum of 12v and also be rated at least IPx7 which means it is totally immersion proof.
Bathroom Zone 1
Zone 1 is the area above the bath or shower tray to a height of 2.25m from the floor. Any fitting used in this zone must have a minimum rating of IPx4* , which means it is protected against water spray from all directions. If the fitting uses a 240v supply, a 30ma residual current device (RCD) must also be used to protect the circuit in this zone.
Bathroom Zone 2
Zone 2 is an area stretching 0.6m outside the perimeter of the bath and to a height of 2.25m from the floor. In this zone again an IP rating of at least IPx4* is required. It is good practice to regard the area around a wash basin, within a 60cm radius of any tap as zone 2.
Bathroom Zone 3 (Outside Zones)
Zone 3 is anywhere outside zones 0, 1 and 2 (subject to specific limits) and where no water jet is likely to be used. No IP rating* is required in these areas.
*If there is any likelihood of water jets ever being used for cleaning purposes in Zones 1,2 and Outside Zones, fittings rated a minimum IPx5 must be used which tells you that the fitting is protected against water jets.
The latest edition of the IEE wiring Regulations will provide more detailed information but your electrician should be fully up to date with these.
When it comes to selecting the actual fittings to go into the different bathroom zones there are plenty to choose from in our Bathroom Lighting category.
Need Further Advice?
The information provided in this guide should help you to understand the requirements for bathroom lighting and the meaning of bathroom zones. When you discuss your requirements with your electrician you should now feel able to do so with greater confidence than you may have felt before.
If you have any further questions please don’t hesitate to get in touch:
- Call us: 0345 6461142
- Email us: firstname.lastname@example.org
Why not take a look at our full range of Bathroom Lighting?
For more inspiration and advice try our Lighting Advice section.
Charles Barnett Managing Director
Charles started Lyco in 1995 with just 4 enthusiastic employees and has grown it considerably over the past 25 years. Charles is also the Managing Director of Lighting Direct and newly acquired Online Lighting. He now has a team of 50 lighting experts working on growing Lyco Group to be the UK leader in lighting for both businesses and homes. Away from the office he is a keen cyclist and is proud to have cycled 1017 miles from Lands End to John O’Groats to raise money for a new residential centre for adults with multiple learning difficulties.